Outline the steps necessary to setup the QCXxx-F (-FM) controllers for Ethernet IP.
All users of QCXxx-F (-FM) controllers integrating with an Ethernet IP Master PLC.
-From the Main Menu go to Settings-Fieldbus
-In the Type dropbox select Ethernet IP
-Enable Bus Control and Logs
-Under Input click on one of the Bits to open the Input Bit Assignment Screen.
-Select the required Data for each Bit and select Apply.
-When all Bits are assigned select OK at the bottom of the screen.
-Follow the same procedure to assign the Output Bytes.
-After the Input and Output Assignments are programmed select the Save icon in the top right corner.
-From the Main Menu go to Settings->Ethernet Settings.
-Assign the appropriate network settings for Port 2 to communicate with the PLC and select the Save icon in the top right corner..
--Note: Port 1 is used for accessing the controller web browser and should be on a different subnet than Port 2.
--Note: There is an option on the Fieldbus Setup screen to select the PCM Profile. Enabling this will set the Input and Output Bits to the same mapping as the PCM controllers.
See the attached link for the appropriate EDS file. The controller should be updated to version 1.1.6 or greater before using the Ethernet IP option.
See the attached spreadsheet showing the PCM Bit Mapping.